Installation Notes for 48V 100Ah Rack Type LiFePO4 Battery
Time of issue:2023-01-13 11:37
The 48V 100Ah Rack Type LiFePO4 Battery is an important basis for maintaining stable power supply during the power supply process. However, there are still many problems in the installation and use of the current 48V 100Ah Rack Type LiFePO4 Battery. Because many equipment in computer rooms and hospitals cannot be powered off, Many companies will equip their instruments with 48V 100Ah Rack Type LiFePO4 Battery, so how to connect the UPS power supply?
Connecting the 48V 100Ah Rack Type LiFePO4 Battery to the grounded AC input power supply must have an appropriate branch circuit protector (circuit breaker). Connecting it to any other type of socket may cause electric shock injury.
In order to reduce the risk of electric shock caused by poor grounding of the load equipment, when installing the computer interface signal line, the AC input power supply must be cut off, and the power supply must be connected only after all signal connectors are connected.
The area where the 48V 100Ah Rack Type LiFePO4 Battery is placed should have adequate ventilation, away from water, flammable gas and corrosive agents.
The Rack Type LiFePO4 Battery should be placed near the mains input socket so that the mains input plug can be unplugged and the power cut off in an emergency.
The input socket of the 48V 100Ah Rack Type LiFePO4 Battery should be connected to the mains, and the output socket can be connected to the computer and monitor through the wiring board.
Keyword:48V 100Ah Rack Type LiFePO4 Battery,48V 100Ah Rack Type LiFePO4 Battery products,48V 100Ah Rack Type LiFePO4 Battery manufacturers